The 2116 Alarm Kit affords a simple and economical means of providing the 2100 series exit device
with an audible alarm. This alarm is battery operated and completely self-contained. It serves as the
hinge stile mounting bracket for the 2100 series exit device and operates when the device flat bar is
depressed. It can be retrofitted to any existing 2100 series exit device. The Alarm Kit has a non-ferrous
cover which is spray finished to match the exit device.
Kit incorporates a solid-state circuit with electronically generated alarm. Powered by the supplied 9
VDC transistor battery.
Alarm kit requires only drilling and tapping 3 holes. Can be retrofitted to existing 2100 series exit
Loud Alarm Db Level:
Alarm sounds loud, piercing tone (measures 90 to 96 decibels (Db) at 10 feet).
A mortise cylinder (not supplied unless specified) arms and disarms the alarm. A Red LED indicator
will illuminate every 30 seconds when the alarm is armed and in stand-by.
Arming Delay/Authorized Egress:
10-second delay (after arming) permitting egress (by turning key clockwise).
Removing cover will activate alarm. Battery is protected by a hardened steel shield. Alarm will
continue to sound even when alarm switch wires are cut.
Factory preset for instant alarm. Selectable feature for alarm to sound when exit device touchbar is
depressed for more than 2 seconds. (This feature is selected by a switch on the circuit board.)
Alarm is armed by turning key clockwise. Low audible chirp indicates alarm has been activated.
Alarm will sound when the exit device touchbar is depressed. Factory preset for standard alarm
mode which automatically resets after 5 minutes.
Continuous Alarm Mode:
Alarm sounds continuously when the exit device touchbar is depressed. Alarm must be manually
reset by keyswitch. (This feature is selected by a switch on the circuit board.)
Low Battery Drain:
On stand-by conditions (with few or no alarm activations) battery life is approximately one year.
Low Power Battery Indicator:
The electronic circuit will sound an audible beep every 30 seconds when the battery power drops
below a safe operating level.
larm Kit is complete
2-1/2" high, 2-3/8" deep, 7" long
Chassis, stainless steel; cover, non-ferrous.
Mortise cylinder. Clockwise turn arms the alarm; counterclockwise turn disarms or silences the alarm. (Cylinder not included.)
630, 689, 691, 693, 695